If you plan to extend your home or upgrade existing wiring, keeping within the safety limits for each circuit you install is essential. Pushing the boundaries of a circuit or a circuit breaker has potentially dire consequences for health and safety in your home.

**Up to 10 outlets can safely run on a 20-amp circuit. A circuit should not run at more than 80% of its load capacity. On a 20-amp circuit, this is 16 amps. The rule-of-thumb is one outlet for every 1.5 amps of the 80% maximum. The total draw on a 20-amp circuit should not exceed 16 amps.**

The intention for the design of each circuit in your home is to handle a specific current draw. This maximum current is dependent on the wiring installed for the circuit and the size of the circuit breaker connected. Ensuring the wiring is safe and preventing overloading is an easy matter, provided that you stay within the specified limits for the circuit. We will show you how to make sure your 20-amp circuit is not overloaded.

## How Many Outlets Can You Put On a 20-Amp Circuit?

The wiring and the installed circuit breaker are the defining components that determine the amperage load that the circuit can handle.

When planning the home’s circuitry, each circuit is sized, including wire gauge and circuit breaker size, for the expected size and type of appliances connected to the circuit.

**According to the American Wire Gauge or AWG standard, the minimum wire gauge size for a 20-amp circuit is 12-gauge. Connecting a 20-amp circuit breaker to the 12-gauge wire creates a circuit rated as a 20-amp circuit.**

**Here is a quick wire-gauge chart for standard circuit sizes for your convenience.**

Circuit | Wire Gauge |
---|---|

15-amp | 14-gauge |

20-amp | 12-gauge |

30-amp | 10-gauge |

40-amp | 8-gauge |

50-amp | 6-gauge |

60-amp | 4-gauge |

How do you know the number of receptacles or outlets you can connect to the circuit? The answer is quite simple and can be derived using a basic calculation. The NEC or National Electric Code stipulates that a circuit can draw continuous current up to 80% of its rated load.

**On a 20-amp circuit, the 80% continuous capacity rule restricts the maximum constant current to 16 amps. The calculation to work this number out is as follows.**

20 amps * 0.8 = 16 amps

The NEC provides leeway for appliances drawing a spike current that will exceed this 80% limit for a short time but not for extended periods. The reasoning is that a constant current draw close to the circuit’s maximum capacity will cause the conductors in the wiring to generate heat, which can potentially pose a safety risk.

**A rule-of-thumb measure establishes how many outlets you can connect to the circuit without exceeding the 80% usage limit. This measure is one outlet for every 1.5 amps up to the 80% maximum usage. Here is the calculation for our 20-amp circuit.**

16 amps / 1.5 = 10.66 outlets

**We round down the calculation result down to achieve our ten outlet maximum on a 20-amp circuit.**

### What If You Want More Than 10 Outlets On a 20-Amp Circuit?

**When there are insufficient electrical outlets in a room in your house, the possibility of overloading a circuit becomes a genuine problem.**

The first thing most people do is purchase an extender plug that allows them to connect multiple devices to a single outlet. The extender may seem like a solution to limited outlets, but it can be dangerous, particularly if the extender plug itself does not have any overload protection.

**The best option in this circumstance would be to split the number of circuits over two 20-amp circuits. For example, if you need 12 outlets, the best solution would be to install two 20-amp circuits and put six outlets on one circuit and six on the other. This split will give you capacity on both circuits for future expansion, should you need it.**

## How Many Outlets and Lights Can You Put On a 20-Amp Breaker?

**It is preferable to keep lights and outlets on separate circuits. The NEC allows for connecting light-fittings to a 20-amp circuit, but it is best to put lights on their own, independent circuit from a practical point of view.**

**The general standard is to wire lights on 15-amp circuits and outlets on 20-amp circuits. However, it is possible to wire a light into a 20-amp circuit and be within code.**

If you decide to go this route, it does not change the circuit’s number of outlets. Each light that you include in the wiring would take the place of one outlet.

Thus, if you wanted to include two light fittings in the circuit, you would have the scope to install eight electrical outlets for a maximum of ten outlets.

To summarize, the sum of outlets and lights on the circuit must not exceed ten, the maximum number of outlets allowed on the circuit.

## What Can Run On a 20-Amp Circuit?

The intention of 20-amp circuits is not for running heavy-duty household items such as cooktops, stoves or high capacity refrigerators or washing machines, and dryers.

**20-amp circuits are suitable for running smaller household appliances. The NEC requires at least two 20-amp circuits installed in a kitchen for the countertop. This regulation caters to medium-duty kitchen appliances used at the countertop level without overloading the outlets.**

**The following devices and appliances can connect to 20-amp circuit outlets.**

**Microwave ovens.****Blenders.****Toasters.****Mixers.****Home entertainment systems.****Television.****Freestanding lamps.****Vacuum cleaners.**

Even though the number of outlets on a 20-amp circuit can be the appropriate number, it is possible to overload the circuit at the outlet point. Many people plug too many devices into the outlets with extender plugs.

**It is crucial to ensure that the total Watts on the system does not exceed the circuit wattage. You can calculate the maximum wattage that can run on a 20-amp circuit with the following equation.**

Max amps * volts = watts

16 amps * 120 volts = 1920 watts

**The figure of 1920-Watts represents the maximum wattage that can run on the circuit.** Using this number as the upper limit, we can tally up the Watts of all the devices connected to the outlets. You can find the Watts that each device uses printed on the service plate for each device.

Tally up the Watts for each device connected to the circuit. **This total should be less than the total number of Watts allowed on the circuit, which, in the case of a 20-amp circuit, is 1920-Watts.**

## Conclusion

The maximum number of electrical outlets you can run on a 20-amp circuit is ten. Ten outlets will power devices and appliances without exceeding the 80% capacity rule for residential electrical wiring.

If you need additional outlets, the best solution would be to install a second 20-amp circuit and divide the number of outlets equally across the two circuits.

Overloading a circuit is a dangerous practice, so if you are unsure of your wiring or calculations, run them by a qualified electrician for confirmation.

## Sources

- 15 Or 20 Amp Outlets? Everything You Need To Know
- How Many Outlets Can Be Placed on a 20 Amp Household Circuit?
- How Many Outlets on a 20-Amp Circuit? Find the Answer Here!

HomeInspectionInsider.com is owned and operated by Hubert Miles is a participant in the Amazon Services LLC Associates Program, an affiliate advertising program designed to provide a means for sites to earn advertising fees by advertising and linking to Amazon.com. HomeInspectionInsider.com also participates in affiliate programs with other affiliate sites. Hubert Miles is compensated for referring traffic and business to these companies.