Many homeowners do not understand the science behind the electrical circuit installation, resulting in unsafe changes made to the electrical system. It may seem like a simple, easy solution to install a 20-Amp breaker in the place of a 15-Amp breaker, especially if the breaker is continuously tripping, but is this a safe solution?
You can change a circuit breaker for 15-Amp to a 20-Amp breaker if your wiring is of the correct rating. 15-Amp circuits are often used for lights, and 14-gauge wire is used, which is not rated for a 20-amp circuit breaker. If the wiring is 12-gauge, you can replace the breaker with a 20-Amp breaker.
Homeowners who like to DIY problems in their homes may consider swapping a 20-Amp breaker for a 15-Amp breaker to be a solution to remedy various electrical issues, from adding additional outlets to stopping a 15-Amp breaker from tripping continuously. Can you change a circuit breaker from a 15 to 20-Amp? Let’s discover the answer to this question and why it may not be a good idea.
How Do You Change A 15 Amp Breaker To A 20 Amp Breaker?
Changing a 15-Amp breaker to a 20-Amp breaker is a reasonably simple task to complete, but it should only be changed to a 20-amp if the circuit is designed to carry that level of current. It only takes a few essential tools and the replacement breaker to get the job done.
The tools you will need to do the job include the following.
- Insulated gloves, preferably rubber, for additional safety
- A flathead screwdriver
- A non-contact voltage meter or a multimeter
- 12 gauge wire
- A headlamp for additional lighting
Complete the following steps to change out the breaker from a 15-Amp to a 20-Amp.
1. Switch Off The Mains Supply
It is always safer to work with no current flowing through any of the circuits in the breaker panel. Switch off the mains supply switch before opening the panel.
2. Open The Breaker Panel
Put on your insulating gloves and use the flat head screwdriver to unscrew the cover plate from the breaker panel box. Hold the cover plate in place with one hand while you remove the last screw to prevent the cover plate from falling when the last screw is removed.
If the plate falls to the floor, it can get bent and difficult to fit back in place.
3. Make Sure The Wire Gauge Is Correct.
Examine the wire gauge on the circuit where you want to replace the breaker. If the wire is 14-gauge, sometimes referred to as #14 AWC, then you cannot place a 20-Amp circuit breaker in this circuit.
If you want to continue with the replacement, you will need to replace the circuit witing with a 12-gauge wire. Fitting a 20-Amp circuit breaker to a 14-gauge wire will contravene the NEC and pose a serious safety risk for your home.
If you are unsure how to tell the difference between the two-wire gauges, the 14-gauge wire is 0.06-inches thick, while the 12-gauge wire is 0.08-inches thick.
4. Release The Old Circuit Breaker
Use your headlamp for extra lighting for this step, particularly if the breaker box panel is in a dark location. Use your multimeter of contactless volt-meter to make sure none of the wires are carrying any current.
Undo the screws holding the wires in place on the circuit breaker and push them to the side, so they are out of the way. Depending on your circuit breaker type, unclip or unscrew it for the breaker box panel housing.
5. Fit The New Circuit Breaker
Clip or screw the new circuit breaker into place, and connect the wires to the new circuit breaker. Once the wires are connected, switch on the mains supply switch and switch on your new breaker.
Use the multimeter to check the voltage across all the circuit breakers to ensure that your voltage across the new breaker matches the other breakers. This will indicate whether your new circuit breaker is allowing the correct voltage through it.
6. Close Up
Switch off the mains supply once again and replace the breaker box cover plate. It is safer to do this with the power off to prevent a screwdriver from slipping and touching a hot wire.
Once the cover plate is back in place, switch on the mains supply breaker and ensure all circuit breakers are switched on, including the newly replaced one.
Can You Upgrade A Circuit Breaker?
You can upgrade a circuit breaker to a new design circuit breaker as long as the new breaker will fit in the mountings in the breaker box and the breaker is rated for the same amperage as the original breaker.
You can upgrade your breaker to a higher amperage-rated breaker as long as the wiring in the circuit is of the correct gauge. A 12-gauge wire is required for a 20-amp circuit breaker.
Can I Install A Larger Circuit Breaker?
You can install a larger circuit breaker on a circuit if the physical wiring is rated for the larger breaker. In many homes, the contractor who wired the home will use a lighter gauge wire for circuits that draw less current, such as the light circuits. The 14-gauge wire used for these circuits is easier to pull through the ducting and cheaper.
Other contractors will use 12-gauge wire throughout the house, even on the 15-Amp circuits. This variance in wiring gauges requires you to ensure the circuit has the correct gauge wire for the larger breaker. A 20-Amp circuit breaker requires a 12-gauge circuit wire to be compliant with the NEC and for safety.
Can You Put A 20A Outlet On A 15A Circuit?
It is theoretically possible to put a 20-Amp outlet on a 15-Amp circuit because the 15-Amp breaker will protect the circuit should the 15-amp limit be exceeded.
According to Table 210.21(B)(3) of the NEC, installing a 20-Amp outlet on a 15-Amp circuit is not permitted. Doing so will make the electrical wiring of your home non-compliant with the NEC.
This example shows that if a configuration works in theory, it may not necessarily be compliant with the code.
The regulations contained in the NEC are put in place to ensure safe practices are used when using electricity in the home. You should not make changes to the electrical system in your home that contravene any of these regulations since they are there to make the systems safer in the house.
Consequently, you should only replace a 15-Amp breaker with a 20-Amp breaker in a circuit if the wiring complies with the requirement of 12-gauge wire for a 20-Amp circuit breaker.