I’ve come across a lot of electrical issues during home inspections. I hear the most common question: “Are Federal Pacific breaker panels safe?” Federal Pacific Stab-Lok breaker panel, also known as the FPE Stab-Lok breaker panel, has always been a significant concern for me.
Federal Pacific breakers and electric panels (FPE Stab-Lok) have a high risk for unexpected circuit breaker failure. These breaker panels have high failure rates linked to thousands of house fires; thus, they are considered defective and unsafe by most inspectors and electricians.
The common stance among home inspectors and home inspection certification organizations, like NACHI and ASHI, is that Federal Pacific Electric breaker panels need replacing. Homeowners with a Federal Pacific Electric panel should update their electric panel box.
Get FREE quotes from licensed electricians in your area today. Whether you need an outlet or ceiling fan installed or a new electrical panel or wiring, We Can Help! All electricians are screened, licensed, and insured.
The safety of the Federal Pacific circuit breaker panels has been a major ongoing topic for many years now.
There seems to be much controversy about them, and there is a good reason for that. However, what does that mean for future homeowners that stumble upon a house with a Federal Pacific breaker panel?
Federal Pacific Electric Stab-Lok breaker panels are dangerous and a latent fire risk. Consider these facts:
- The Consumer Products Safety Commission identified Federal Pacific Electrical panels as a latent safety hazard over 40 years ago. However, there are still over 25 million FPE panels in residential homes and commercial businesses in the United States.
- Federal Pacific breakers fail to trip over 25% of the time when a 135% electrical surge is detected. The CPSC found that subsequent electrical surges increase failure rates to 65% or more.
- Based on the information collected from fire reports, Federal Pacific Stab-Lok panel failures cause about 2,800 fires, 13 deaths, and $40 million in property damage annually in the United States.
Since this is a big topic, everyone, including real estate agents, must understand how a Federal Pacific circuit panel affects them. This might be a deal-breaker, while for others, not so much.
What is a Federal Pacific Electric Breaker Panel?
Reliance Electric, the parent company for Federal Pacific Electric Company (or FPE), produced some of the most widely used circuit breakers in North America between 1950 to 1980. You can find Federal Pacific Stab-Lok circuit breaker boxes in homes built until 2000.
Federal Pacific Electric stopped manufacturing FPE Stab-Lok electrical products under its name and eventually sold the name rights. By this time, contractors had installed FPE Stab-Lok breaker boxes in millions of homes.
Other companies purchased the name rights to continue manufacturing Stab-Lok products under different names. These companies continued to manufacture Stab-Lok breaker panels and breakers until around 1990.
Two companies still hold name rights to manufacture Stab-Lok. You can still buy an FPE replacement circuit breaker from:
- Connecticut Electric – produces breakers under the name UBI
- Schneider Electric – produces breakers and panels under the name Federal Pioneer.
You can still find FPE panels in millions of homes. Some suggestions have pointed towards up to 28 million FPE Stab-Lok breaker panels installed worldwide. (1)
While installing a replacement circuit breaker is better, a complete electrical panel replacement is best. Experts found that these panels did not provide proper protection and meet safety standards, as claimed.
Stab-Lok Breakers: The CPSC Recall Stance
The Consumer Product Safety Commission (or CPSC) had to take a stance on the issue; as a result, they started an investigation.
However, in 1983, they had to close their investigation, which had been running for nearly two years.
They could not reach a clear conclusion and found it impossible to initiate a product recall.
Due to insufficient data and budget issues, the CPSC staff could not confirm or discard the claims regarding the safety of the FPE breakers. (2)
Although the breakers failed to meet the UL (Underwriters Laboratories, Inc.) requirements, as we found out later, at the time, the CPSC couldn’t connect these failings with increased safety hazards in the home environment.
In 2012, an IEEE-published study and later various studies confirmed the fire hazards from FPE Stab-Lok equipment & called for CPSC to take appropriate action to caution the industry & consumers. (3)
The Federal Pacific Electric Class Action Lawsuit
Due to the high circuit breaker failure rate to provide appropriate protection to homeowners in 2005, lawyers filed a class-action lawsuit against FPE.
Claimants hired an expert to conduct an extensive investigation of how FPE circuit breakers performed. The results were very concerning as their circuit breakers failed to trip at higher rates consistently across all tests compared to other UL-rated breakers.
As a result, the New Jersey State Court ruled that FPE “violated the Consumer Fraud Act because FPE knowingly and purposefully distributed circuit breakers which were not tested to meet UL standards….“
According to the New Jersey State Court, Federal Pacific Electric did commit testing fraud and a cover-up by claiming that their defective circuit breakers met UL standards, which was anything but genuine.
Today the Federal Pacific Electric Company is no longer in business.
What is the Purpose of an Electrical Circuit Breaker?
Today every home has electricity, and while it is vital for our wellbeing and comfort, it can also be deadly if mishandled.
Circuit breakers are one of the most important safety devices on any property. They protect our homes in cases of circuit overloads, short circuits, outside power surges, and more. They do it by immediately cutting out the power to the circuit.
If too much current starts flowing through the wiring and the electrical breaker fails to stop that on time, there is a high risk of starting an electrical fire.
What Happens if a Stab-Lok Breaker Fails to Trip?
A few significant hazards arise from electrical breakers that do not work correctly.
Suppose a lot of power flows through the electrical circuit, and the breakers don’t trip. In that case, nothing stops the electricity from melting the wiring and anything nearby.
The electrical panel can overheat, making the breaker unable to close the electrical circuit and protect it from overheating. At the same time, the circuit breaker itself will overheat and catch fire. The following electrical fire is exceptionally hazardous to the property and its occupants.
Are Federal Pacific Breakers Dangerous?
So many FPE breakers are not working as intended because of their original design, specifications, and the cheap materials used in their production.
Two aspects of the FPE panels make them a significant electrical fire hazard for any home.
1. Federal Pacific Stab-Lok Breaker Failure Rates
The main reason they are hazardous is their high rates of not tripping when they should.
The US Consumer Product Safety Commission (CPSC) concluded that when energizing the breakers on both poles at a 135% overload, they failed 25% of the time. When energized on individual poles at the same overload, the failure rates jumped to 51%.
These are already concerning numbers, but it doesn’t stop here, as we will find out.
After being switched on and off, the failure rates jumped even more across all breakers. In the first case, the failure rates jumped from 25% to 36%, and in the second case, from 51% to a massive 65%! (4)
In addition to this, there are high rates of lock-up happening. A lock-up is when a switch, once tripped, will never trip in the future, regardless of the electrical overload. Even if you try to switch them off and on, they will not trip – it is as if your home doesn’t have a circuit breaker anymore.
CPSC did one of the more recent tests of the FPE Stab-Lok with 830 single-pole and double-pole breakers. The results show up to 70% of the double-pole breakers failed to trip in the presence of an overcurrent. And up to 80% of the single-pole GFI breakers failed to trip. And in the case of a second overcurrent, 100% of the jammed double-pole breaker testing did not trip. (5)
Many home inspectors and electricians will tell you the best way to repair an FPE panel is to replace it entirely. Since they don’t work at such alarming rates, there is a severe risk of an electrical fire that you should not overlook.
There have been rough estimates that nearly 2,800 electrical fires each year are caused by a Federal Pacific breaker that did not trip.
2. The Federal Pacific Panel Itself
Not only were the breakers cheaply made, but the panels were too.
Having unreliable circuit breakers was already a big concern, and adding the problematic panels to that makes matters worse.
The bus bars’ quality was of inferior quality to most other manufacturers. Different problems have been reported, such as:
- Arcing at the bus.
- Crowded wires within the panel box.
- Breakers may not stay tightly connected to the bus bar.
- The breakers can remain active even in the OFF position.
- Breakers can unexpectedly trip upon removal of the electrical front cover.
Will a Federal Pacific Panel Pass a Home Inspection?
There has been much debate and varying opinions on this throughout the years. While Federal Pacific Stab-Lok breaker panels are legal under the grandfather law into the electrical code, home inspectors aren’t building code inspectors and look at much more than just the building code when inspecting a home.
Will a Federal Pacific circuit breaker panel pass a home inspection?
Due to known safety concerns, certified home inspectors should recommend Federal Pacific electric panel replacement. It has nothing to do with the building code. It’s about the safety concerns they possess. Most home insurance companies no longer insure homes with a Federal Pacific breaker panel.
Therefore, you should replace the electrical panel before obtaining a new homeowners insurance policy.
First, we need to look at what exactly is a home inspection.
What Does a Home Inspection Cover?
An adequately carried out home inspection is vital for the required due diligence if you buy a new home or property.
A home inspection is a thorough assessment of the home’s condition and will aid you in avoiding any potential issues and hazardous situations that otherwise might go unnoticed.
A qualified home inspector does a home inspection. They will inspect and assess all physically and visually accessible areas of the property and advise any potential issues of concern to any homeowner.
When home inspectors find safety concerns, the inspection report can even give the buyer a chance to negotiate repairs with the seller.
Hence signing a home inspection contingency is vital for protecting the buyer’s interest.
Inspection of the Federal Pacific Panel and Stab-Lok Breakers
We have just discovered that a home inspector will assess the whole house. However, there are certain limitations to the home inspection, as not everything can be seen or reached.
If specific points of concern need further investigation, your home inspector will advise you on hiring a qualified specialist.
When it comes to FPE breakers and panels, they cannot be tested or inspected by either a home inspector or a licensed electrician. The way to accurately assess an FPE breaker’s condition and whether they are defective is by performing a live-current functional test on every breaker in the panel, which requires specialized equipment.
The only way to locate a defective circuit breaker is additional testing by a circuit overload to see if it trips or not.
Another problem stems from performing such tests is usually very expensive and would probably cost more than changing the whole panel.
So we end up in a situation where neither home inspectors nor electricians can answer whether or not a breaker is functioning the way it should.
They can visually inspect them for potential issues and check if the switches work. However, there is no telling if the breaker will trip to that and what will happen afterward.
The Gray Area of Federal Pacific Panels
Even though most licensed electricians and home inspectors stress the importance of replacing FPE Stab-Lok breaker panels, no mandatory recall confirming the panel’s safety concerns is present.
However, every home inspector has to work within certain limitations.
- On the one hand, we have evidence from independent sources that the FPE panels and breakers will trip at as much as three times the rated capacity or, in some cases, will not trip at all.
- On the other hand, we have no official stance from government agencies or regulatory authorities. This means that, technically, they are legal to use.
Here we find ourselves in a bit of a gray area.
As home inspectors, we are obliged to report and inform every future homeowner of the possible safety hazards and problems they might face when buying their new home.
And any FPE panel and Stab-Lok breaker are considered a serious safety hazard.
What if a Home Inspector finds a Federal Pacific Electrical Panel?
FPE Stab-Lok breaker panels have high rates of inability to protect against overcurrent. Since they have such controversial working reliability upon inspection, they are generally considered a “Safety Defect” on the home inspection checklist.
As a home inspector, I am concerned about the safety of my clients. The FPE breakers might work fine for years or even decades, but they might not protect one overcurrent or short circuit.
The breakers can appear functional but be melted to the bus bar. There is no way of telling which FPE breaker is bad.
Home inspectors should point out that they are a latent safety hazard and advise replacing the panel with a licensed electrician. Some electricians even refuse to work on such panels to guarantee what will happen in the future.
They are not legally recognized as a fire hazard, as even the CPSC could not come up with a conclusive answer. However, since these breakers have shown such high failure rates, you should replace them as soon as possible.
Although an FPE panel would pass the home inspection from a certain point of view, every home inspector would advise you to face certain risks and hazards.
How to Identify Federal Pacific Panels and Breakers?
The first thing to point out is that since the FPE Company is no longer operating, the only way to come across Federal Pacific breaker panels is through buying (or renting) a house with an existing FPE panel.
The Federal Pacific panels and breakers are no longer available in stores. A new replacement breaker is available under various brand names, like Connecticut Electric and Federal Pioneer. We advise against buying used Federal Pacific circuit breakers from eBay, salvage yards, and third parties.
Due to the potential danger, every homeowner and homebuyer will benefit from recognizing a Federal Pacific panel and breaker when they see one.
Despite the Federal Pacific being out of business for a long time now, the aftermath of their actions is still very real.
If you are buying or owning a home between 20 and 70, there is a good chance you might have a Federal Pacific panel installed.
You need to take several key steps when assessing the type of breakers installed.
- Look for any labels or logos on the front cover of the panel. An orange and white label saying FPE, Federal Pacific, Federal Pacific Electric, Federal Pioneer (in Canada), or other variants of these words would mean that you indeed have an FPE panel.
- Look for any labels on the breakers. If this is an FPE panel, there will probably be the name Stab-Lok printed inside of the panel.
- The breakers will also have the signature red label across their front. The color might be blue in some FPE panels in Canada.
What to do if You Have a Federal Pacific Panel?
If you find a Federal Pacific panel and Stab-Lok breakers, you should call a certified electrician and get a thorough inspection of the home’s electrical system.
However, since this is considered a significant safety concern, the best thing to do is always to have the panel replaced.
In the meantime, it is essential to take specific safety measures to avoid creating more hazardous situations.
I recommend you do the following:
- Make sure you have installed and working smoke detectors.
- Find the heaviest loaded electrical circuits in your home and reduce their load by unplugging some of the devices connected to that circuit.
- Do not overload the electrical circuit. Be careful not to connect too many appliances on the same circuit and avoid connecting high current demanding appliances to the same circuit or circuits with low amperage. You want to avoid having the breakers trip.
- Repair or replace faulty breakers or electrical equipment in poor condition or behaving oddly.
- Get familiar with how the electrical circuits you own or manage are set up in the property. Keep track and know which electrical appliances are connected to each circuit.
- In case of a problem, disconnect any electrical appliances immediately, cut out the electricity in the circuit, and have the appliances and wiring inspected by a licensed professional if an FPE breaker trips, make sure to have the panel checked thoroughly by a certified electrician.
Ensure you comply with the local codes if changing the wiring or panels. In our article, Signs Your Electric Panel Needs an Upgrade – Safety & Costs to Replace, we discuss determining if it’s time to upgrade your electrical panel.
So the two options people generally face are replacing the whole electrical panel or the individual breakers themselves.
Let’s go through the two options and explore their pros and cons:
1. Should You Replace a Federal Pacific Panel?
When homeowners first stumble upon the potential dangers of having an FPE panel in their homes, their main concerns are what they should do. Should FPE panels be replaced entirely, or can you switch the FPE breakers with replacement breakers?
However, any homeowner who stumbles upon one of these should know that replacing the entire panel and circuit breakers with newer units is the best course of action.
Homebuyers should be mindful of these panels when house hunting since replacing them can cost between $1500 and $3000.
2. Should You Replace a Federal Pacific Stab-Lok Breaker?
Replacement FPE Stab-Lok circuit breakers are unlikely to reduce the failure risk of this equipment. We recommend that residential FPE Stab-Lok electrical panels be replaced entirely or the entire panel bus assembly be replaced, regardless of FPE model number or FPE year of manufacture.Source: https://inspectapedia.com/fpe/FPE_History.php
Replacing the Federal Pacific breaker is not recommended as this will not improve the fire hazard they pose to your property.
We have many studies confirming the dangers of using FPE breakers. No data would suggest that even a newer FPE breaker would offer different safety levels than the original ones.
In addition to that, more concerns go beyond individual breakers. FPE panels have been known for having panel bus bar damages, meltdowns, and in some cases, breakers not being able to stay secured safely on the panel’s bus bar.
However, if you can’t afford to replace the panel and it is not damaged, aftermarket breakers are available that are better than the older breakers.
The Federal Pacific replacement breakers from Schneider Electric are for Federal Pioneer panels in Canada. Connecticut Electric replacement breakers are available in the United States for Federal Pacific Electrical boxes.
However, Dr. Jesse Aronstein has reviewed the Schneider Electric and Connecticut Electric replacement breakers and found problems with failure rates.
Avoid buying or using old breakers from other panels or salvage shops.
Cost to Replace a Federal Pacific Stab-Lok Breaker Panel
Replacing a Federal Pacific panel will vary depending on its size, the number of breakers, amperage, and location.
So, how much does replacing a Federal Pacific Stab-Lok breaker panel cost? Usually, replacing a Federal Pacific Stab-Lok breaker panel costs about $1500-$2000. However, the circuit breaker panel replacement often accompanies other repairs to meet current electrical codes.
When replacing an FPE Stab-Lok circuit breaker panel, there are additional costs. Most FPE Stab-Lok panel replacements will require:
- Relocation to an area of the house that meets clearance requirements for local electrical codes
- Installation of arc fault and ground fault breakers (See information on AFCI code requirements and GFCI code requirements)
- Wiring upgrades for some or all branch circuits
- Installation of the main service disconnect
- Upgrading the 3-phase main service entrance wire from the meter base to the panel to 4-phase wiring
Unfortunately, the high cost of changing an FPE panel often discourages homeowners from replacing it, but so can the cost of not doing it.
Even worse is replacement installations where contractors took shortcuts to save money, which causes more safety problems than leaving the FPE panel alone.
If you have an FPE panel and want to replace it, you need to consult with a licensed electrician to get a quote.
How to Determine if a Federal Pacific Breaker Works?
Maybe you have encountered an FPE panel and are wondering how to test whether the federal pacific breakers work.
They pose a severe fire hazard but are tough to test – usually, there is no way of knowing if they work or for how long. You can inspect the panels for any signs of overheating or scorching. You can check to see if the breakers are also secured and attached to the bus, you can switch them on and off, but this will not give away a faulty FPE breaker.
Each breaker needs to be tested by overloading it past its rating and seeing if it will trip. However, this is a potentially unsafe practice and is not ordinary by home inspectors or licensed electricians.
Another concern is that even exercising the breakers by switching them on and off has not improved their reliability.
Before replacing a federal pacific breaker, you can check the circuit with a multimeter.
How do Federal Pacific Electric Panels Affect Home Insurance?
In recent years, home insurance companies have begun ordering 4 Point Inspections on homes 30 years of age or older to control the insurance company’s risk exposure.
One of the inspection sections asks for information about the electrical system, including the type of electrical panel and breakers present, and is a home inspection red flag that could cause you a problem during underwriting.
Insurance companies have received more claims for electrical fires started from FPE panels and consider them high risk.
Suppose you are considering buying a home that has FPE breaker panels installed. Your home insurance company may:
- Refuse to write the insurance policy until you replace the electrical panel.
- Charge you a higher rate due to the inherent risk they are assuming.
- Terminate your coverage or give you 30 to 90 days in which you need to replace the panel and provide evidence of replacement.
Other panels with safety issues include the Zinsco panel. See our article Are Zinsco Electrical Panels Safe? Dangers & Cost to Replace for details about the inherent problems with Zinsco panels.
You may also be wondering how long electrical wiring in a home lasts. In the article How Long Does Electrical Wiring Last in a Home? We discuss various wiring types and how long they’ll last.
Federal Pacific Electric Panel FAQs
Is Federal Pacific Still in Business?
No, Federal Pacific Electric Company is no longer in business. Federal Pacific Electric Company eventually sold its US circuit breaker business, including the US STAB-LOK trademark, to Challenger Electric. The Canadian registration of STAB-LOK was assigned to Pioneer in 1986.
Are Federal Pacific Panels Illegal?
It’s not illegal to have a Federal Pacific panel in your home. The CPSC never issued a formal recall but warned about the breakers’ problems and their risk to property and personal safety.
The panels are a safety hazard because they didn’t meet modern safety standards 40 years ago, and those standards have only expanded since to include arc-fault and ground-fault protection.
Due to the latent fire hazard, most property insurance companies have “blacklisted” Federal Pacific panels. They often deny coverage or rate the policy to reduce their risk exposure. They usually give you 30 to 90 days to replace the FPE panel or lose coverage.
What Breakers are Compatible with Federal Pacific?
The only breaker currently made to be compatible with a Federal Pacific electrical panel is the FPE replacement breaker from Connecticut Electric. It’s not wise to try and force a Square D, Seimens, or Cutler Hammer breaker into a Federal Pacific panel.
Will a Federal Pacific Breaker fit in a Federal Pioneer Panel?
A Federal Pacific breaker may fit a Federal Pioneer panel, depending on when it was made. However, replacing a Federal Pioneer breaker with a used Federal Pacific breaker is not good. Using a replacement breaker from Schnieder Electric for your Federal Pioneer panel is best.
Where can You Buy Federal Pacific Replacement Breakers?
You can purchase Connecticut Electric and Schneider Electric brand new replacement breakers for Federal Pacific from home stores like Lowe’s or Home Depot.
Get FREE quotes from licensed electricians in your area today. Whether you need an outlet or ceiling fan installed or a new electrical panel or wiring, We Can Help! All electricians are screened, licensed, and insured.